This article covers a commercial leak repair in Drayton Valley and also includes a follow-up service call. Photos relating to both service calls are supplied. Roof Report, June 7, 2011: First I met with the manager on-site and examined the leak areas from the inside. Then I went onto the roof and began examining the suspect areas around RTU (rooftop unit) #4 and RTU #6. I found loose curb stripping under the flashing but was unable to repair at that time due to heavy rainfall. I advised the manager that I would return the next day. Roof Report, June 8, 2011: I informed the staff on-site that I would be working on roof. Then I went onto the roof and removed and replaced the flashing. Lastly I repaired the stripping with ModBit compatible mastic (2 tubes). Follow-up, June 12, 2012: The following email was sent by the client's maintenance manager prompting a follow-up service call:
In speaking with the store, water seems to be entering the store when it rains. From the description the manager noted, it seems the curb flashing on one of the roof top units may require attention as the water is running along side the supply air duct work that protrudes through the roof. Our HVAC vendor was on-site in May to complete an inspection and had not noted there to be any obvious concerns at that time. However, they are not due back until mid-July or so. The area is to the right hand side of the check out area. One ceiling tile is obviously wet. It would be appreciated if you may confirm to have your roofing vendor out within the next day or so while the weather is favourable to make such a repair. Once complete, please do ensure to have any interior water damages as results (ie, water stained or missing ceiling tiles) addressed. Please do advise as to your roofer's anticipated arrival. For the time being the store has been putting a bucket in the area to catch the water whenever it rains. Regards,Roof Report, June 13, 2012: We arrived on-site and inspected the damage from the inside. After gaining access to the roof, we identified the problem area as being an HVAC unit near the southwest corner. To determine exactly where the leak was coming from, we performed a leak test. We brought buckets of water up onto the roof and splashed it all around the HVAC unit. A total of 8 buckets of water were used in this test, but we did not manage to find the problem. It was determined that in order to accurately find the leak we would have to wait for the rain to come. The downspouts appear to be crushed near the bottom, and the northern most down spout seems to be half missing. The pooling of water by the downspouts has to do with the location; the parking lot asphalt where the spouts are is sloped in a way that the water pools by the eastern wall of the building. < End Report > CODE: 5009 Contact Us 24 Hour Emergency Roof Repair. Telephone: 1.403.873.7663. Email: firstname.lastname@example.org. Mailing: 240 – 70 Shawville Boulevard SE Calgary, Alberta. T2Y 2Z3. For all other areas of Canada call 1.877.497.3528 Toll Free. We service all areas of southern and central Alberta and south east British Columbia including Airdrie, Banff, Calgary, Canmore, Crossfield, Carstairs, Didsbury, Olds, Sundre, Three Hills, Drumheller, Hanna, Brooks, Bassano, Strathmore, Chestermere, Irricana, Cochrane, Black Diamond, Okotoks, Priddis, Bragg Creek, Cranbrook, Fernie, Panorama, High River, Vulcan, Medicine Hat, Lethbridge, Taber, Sylvan Lake, Red Deer and other Alberta rural points between.