Below you will find an initial assessment for an ongoing residential site by our Edmonton roofing repair crew. More reports will be posted as they become available. Initial Assessment, July 22 2015: We arrived on-site at 1:00 pm and were lead by the client to two leaks in the shop. One was coming from around the skylight, and another one around the chimney stack in the middle near the edge of the roof. Upon inspecting the roof top-side, we observed that the acrylic MASTIC around the chimney was cracking and lifting in areas. It should be removed and replaced with seam tape and liquid rubber. The penetrations require the same. It is only a matter of time until it begins to leak around the entire skylight. There are also cracks and splits in the skylight, which seems to have had been coated with spray foam. The metal gum box also needs to be topped off. There is a metal boot top-side as well that looks like it was only spray foamed. The roof measurements are 85 ft. long by 51 ft. wide, and the skylight was 4 ft. x 4 ft. It should take 25 man hours to clean and repair the penetrations, apply some gum patch into the metal boot, and cover the foam/top up the gum box with rubber MASTIC. < TO BE CONTINUED > Code: 154 Contact Us Call our 24 hour emergency roof repair at 1.780.424.7663. Mail to: 3428 99 Street NW Edmonton, Alberta T6E-5X5. We service all of Alberta including Edmonton, Stony Plain, Spruce Grove, Fort Saskatchewan, St Albert, Sherwood Park, Leduc, Nisku, Beaumont, Lac La Biche, Grande Prairie, High Level, Westlock, Slave Lake, Edson, Drayton Valley, Devon, Camrose, Wetaskiwin, Tofield, Lamont, Morinville, Vegreville, Tofield, Millet, Calmar, Evansburg, Redwater, Onaway, Viking, Athabasca, High Prairie, Valleyview, Fairview, Peace River, Whitecourt, Mayerthorpe and many more rural areas and towns.