Below you will find roofing reports from the Edmonton roofing repair crew. This client's residential building needs repairs to a low-slope tar and gravel roof. There are some leaks and damage that requires attention, in addition to some work with the gutters and chimney area. Continue reading Tar and Gravel Roofing Repair, August 2015, Edmonton
Below you will find a series of ongoing reports for a residential client in Edmonton, Alberta. The client requires a DuraDek roof skirt replacement. Parts of the flat roof are currently exposed to the elements, so we must examine all exposed areas for damage and ensure that the new installation ties in to the old. Continue reading Flat Roof Skirt Deck Installation, August 2015, Edmonton
Below you will find a series of ongoing reports for a client in Edmonton looking to re-roof their building with an EPDM system. The building is a low slope duplex, where the entire roof would receive treatment with the new surface. Continue reading EPDM Roofing Replacement, July and August 2015, Edmonton
Rooftop Balcony Leak Repair Edmonton - Below you will find a series of ongoing reports for a residential client in Edmonton, Alberta. The client requires leak maintenance where a PVC rooftop deck and a tar and gravel flat roof connect and flat roof recovery or replacement to the tar and gravel flat roof. Project manager notes have also been included. This single family home in Edmonton Alberta has a second story rooftop deck (a deck that is over a heated living space is considered a rooftop deck - it needs a membrane suitable for over heated living spaces such as a flat roof membrane). It issue is the homeowners recently purchased the home and came to realize the second story balcony was leaking in to the home causing significant damage. So they hired a deck company to replace the membrane on the deck, but the decking company could not re-connect the balcony membrane to the tar and gravel roof that runs around the house as a skirt. The home-owner asked us to inspect the tar and gravel flat roof skirt and the need for the rooftop deck membrane to be connected properly (the deck membrane that was recently installed is a PVC and the PVC will not of course bond to a tar and gravel roof so a break needs to be constructed and then both the PVC deck membrane and the tar and gravel roof need to be tied in correctly). They also asked us to inspect the tar and gravel flat roof on top of the house. Update (07-30-2015): More posts to come as the work continues at this site. Update (07-30-2015): Quotation added New Client Call, July 24 2015:
- Service: Roofing
- Type: Residential flat roof
- We have small issue with the roof section that joins up with the deck. There is water infiltration culminating in leaks.
- The flat roof skirt that wraps the house which connects to the vinyl deck needs an assessment for replacement options.
- Most recently, there was a water ingress as the previous decking contractor did not correctly set a temporary waterproof scenario where the deck meets the flat roof skirt. An infrared technologist was called in and said there is no considerable issues in the walls, but considering the flat roof skirt's age there may be an issue with rotting joists or sheathing.
- An inspection is required on the connection area between the vinyl deck and the flat roof skirt. Is there a suitable break between the two sections appropriate for us to roof in the skirt properly?
- Inspect the main flat roof above for any maintenance concerns and estimate the expected life-cycle for future replacement considerations.
- Ask the client for the manufacturer name of the vinyl used for the most recent roof/deck replacement. When a roof deck is installed over a heated living space, there needs to be a product that is intended not only for use as a deck membrane, but also as a rooftop (low slope) roof membrane.
- Tie-in new DuraDek material to tar and gravel roof on both ends
- Tie-in DuraDek material to tar and gravel roof and replace tar and gravel roof roundabout. Choose from EPDM, TPO, PVC, or 2-ply SBS torch-on
- Main flat roof on top is not leaking and does not require repair or maintenance at this time.
Flat Roof Leak Inspection Edmonton - Below you will find a photo journal and emergency roof repair assessment from our Edmonton roofing repair crew at a commercial roofing site. Although the call began as a tar and gravel flat roof leak repair, the extent of damage escalated to the client requesting a quotation for flat roof recovery or replacement options. More field reports will be posted as they become available for this site. Regular Flat Roof Maintenance Will Save You Money. If you own a flat roof it is critical for you to conduct regular inspections, maintenance and repairs as needed. You will save considerable money if you do this twice per year. The reason it saves you money is that a complete flat roof replacement is expensive and 9 in 10 times had maintenance been done the replacement would not be required. If you do not do regular inspections and maintenance you could face a catastrophic failure which has occurred to this roof below. Simple spring and fall inspection and maintenance would have avoided a costly re-roof. Click here for a proper flat roof inspection and maintenance check-list. Emergency Flat Roof Inspection Edmonton, March 29 2014: Flat Roof Leaks. There are multiple large leak problems on this commercial tar and gravel flat roof that are currently being managed with buckets. Flat Roof Ponding. The roof assembly is carrying considerable ponding all over that is definitely a concern with dead weight load on the roof in times of sudden storms or in winter freeze thaw situations. Roof Drains. There are two drains on the roof that are useless; the previous contractors did not sump them properly. Roof Maintenance. Previous roof maintenance contractors did not remove the gravel before using tar to patch spots that needed repair. An excessive amount of tar has also allowed trapped air to cause blistering. Gum Boxes. Four gum boxes were actually near open water, and it was able to get into them. This is also contributing to some of the leaks. Roof Membrane. The tar and gravel roof membrane has become weather cracked from the sun, contributed by an improper ballast spread. If the pea gravel is not covering the bitumen layers the UV of the sun will dry out the bitumen causing it to crack and ultimately leak. Blisters. There is mass blistering of the roof membrane in multiple areas. If they continue, water will enter there as well. Several of the blisters on the roof are cratering water into them. Temporary Flat Roof Repairs. While we were on-site, we attempted to drain as much water as possible. The client called off the temporary repairs since the problems have become greater than simple roof maintenance work. The client has requested a quotation on roof replacement or recovery options. < End Report > Code: 109 Contact Us Call our 24 hour emergency roof repair at 1.780.424.7663. Mail to: 3428 99 Street NW Edmonton, Alberta T6E-5X5. We service all of Alberta including Edmonton, Stony Plain, Spruce Grove, Fort Saskatchewan, St Albert, Sherwood Park, Leduc, Nisku, Beaumont, Lac La Biche, Grande Prairie, High Level, Westlock, Slave Lake, Edson, Drayton Valley, Devon, Camrose, Wetaskiwin, Tofield, Lamont, Morinville, Vegreville, Tofield, Millet, Calmar, Evansburg, Redwater, Onaway, Viking, Athabasca, High Prairie, Valleyview, Fairview, Peace River, Whitecourt, Mayerthorpe and many more rural areas and towns.
This report follows repairs made to both levels of a client's tar and gravel roof. The gravel was removed, the roof itself patched and repaired, all before a thorough coating of liquid rubber was applied. Continue reading Tar and Gravel Roofing Recovery, July 2011, Edmonton
Below you will find an ongoing series of reports for a leak repair in Fort Saskatchewan, Alberta. The site is currently a work in progress. More updates will be posted as they become available. Scope of Work, July 21 2015: Upon arriving on-site, the client advised me about two leak sites - one in the kitchen and one above a light fixture by the washroom. On the roof, there was a major water ponding issue and lack of drainage. There is also a fryer vent that has major dripping onto the rubber. The grease that is leaking out has, over time, started to eat away at it [the rubber]. Structural integrity has been lost, so the next step is to cut out the damaged area and replace it with a 12 ft. x 12 ft. EPDM fixture. The next scope of work would be to install an internal drain, piped in by a plumber. < End Report > Code: 100 Contact Us Call our 24 hour emergency roof repair at 1.780.424.7663. Mail to: 3428 99 Street NW Edmonton, Alberta T6E-5X5. We service all of Alberta including Edmonton, Stony Plain, Spruce Grove, Fort Saskatchewan, St Albert, Sherwood Park, Leduc, Nisku, Beaumont, Lac La Biche, Grande Prairie, High Level, Westlock, Slave Lake, Edson, Drayton Valley, Devon, Camrose, Wetaskiwin, Tofield, Lamont, Morinville, Vegreville, Tofield, Millet, Calmar, Evansburg, Redwater, Onaway, Viking, Athabasca, High Prairie, Valleyview, Fairview, Peace River, Whitecourt, Mayerthorpe and many more rural areas and towns.
Below you will find a photo journal from a commercial contract in High Level, Alberta. The work entailed a TPO flat roof recovery and sloped insulation.Background When a roof reaches the end of its life, our clients are faced with the choice of either a full replacement or a recovery. Roof recovery refers to applying a new system over an existing one when the roof is reaching its end-of-life (1). Depending on climate conditions, preference, or preexisting solutions, a roof recovery may be performed using TPO, EPDM, bitumen, cap-sheets and/or asphalt. Sloped insulation refers to the tapering that exists on an insulation system. As a weatherproofing measure, when precipitation reaches your roof, it will run off into the drain system down the slope. Call us today for a consult on which roof recovery system is right for your commercial, industrial, or residential environment. < End Journal > Code: HIGH Article Topics: TPO Flat Roof High Level Alberta. Contact Us Call our 24 hour emergency roof repair at 1.780.424.7663. Mail to: 3428 99 Street NW Edmonton, Alberta T6E-5X5. We service all of Alberta including Edmonton, Stony Plain, Spruce Grove, Fort Saskatchewan, St Albert, Sherwood Park, Leduc, Nisku, Beaumont, Lac La Biche, Grande Prairie, High Level, Westlock, Slave Lake, Edson, Drayton Valley, Devon, Camrose, Wetaskiwin, Tofield, Lamont, Morinville, Vegreville, Tofield, Millet, Calmar, Evansburg, Redwater, Onaway, Viking, Athabasca, High Prairie, Valleyview, Fairview, Peace River, Whitecourt, Mayerthorpe and many more rural areas and towns.
The report below follows services carried out on a metal roof for one of our industrial clients. They sought GRS' assistance in recovering their roof with engineered liquid rubber, with some other spot repairs to complete as needed. Inspection: June 2, 2011 The GRS crew went on location to inspect the existing roof system and take photos that will help the project management group form a better idea of what service will be needed at this location. The photos appear below. Quotation Delivered: June 6, 2011 After seeing the roofers' investigation photos and measurements, GRS' project management could deliver an accurate quotation for services to be carried out of the roof. Included in the quotation were two separate services; the engineered liquid rubber application and an EPDM installation for the area around two eaves. Also attached to the quotation were the documents and web links surrounding GRS' workmanship guarantee, system methods, schedule availability for the season, and more. There was another note mentioned that regarding schedule availability, it's best to book liquid rubber jobs earlier in the season for when it's warmer. Even though the solution will bond, it performs best when applied in warmer weather. Roof Report: July 20, 2011 The crew went out to the client's building and got to administering trowel-grade liquid rubber to all penetrations, joints, and problematic areas that has been previously discovered. They also did a lap around the perimeter, ensuring watertightness on the high-risk parts of the roof. They then set up the pump to apply the spray-on liquid rubber and managed to cover roughly one-quarter of the roof itself. Their plan was to finish the entirety of the roof the following day, so they packed up the equipment, cleaned the site, and closed the site for the evening. Site Inspection: August 1, 2011 One of the senior members of GRS' crew went on-site to inspect the liquid rubber application and found it to be forming a good seal. There was some water that had formed a small bubble in the rubber, but once popped it was deemed fit for continued use as the rubber still formed a solid barrier to the metal. Roof Report: November 25, 2011 Several months after the initial liquid rubber coating, the client call in to report some other leaks in separate areas of the roof. GRS sent a team out to the site to investigate and carry out the necessary repairs. They administered sealant to the flashing where the wall meets the north-facing roof edge, and again on the south-west corner of the building. They also sealed in the wall-to-roof spots on the west-facing wall and inspected the existing wall spray. After carrying out the spot repairs, they had a better idea of what else needed to be done to the roofing system, and returned the following report:
- The west-facing wall where the windows are is 3' x 78'. Will need 100' x 6" skrim sheet, and roughly 16 man-hours to install it.
- The north-facing wall is 3' x 40'. Need 50' x 6" skrim sheet for another 12 man-hours to install.
- The west-facing wall's upper roof is 3' x 24'. Need 25'x6" skrim sheet and 10 man-hours to finish.